Design+Builder+-+Cooling+Design




 * Building || Block || Zone || Design Capacity (kBtu/h) || Design Flow Rate (ft3/min) || Total Cooling Load (kBtu/h) || Sensible (kBtu/h) || Latent (kBtu/h) || Air Temperature (∞F) || Humidity (%) || Time of Max Cooling || Max Op Temp in Day (∞F) || Floor Area (ft2) || Volume (ft3) || f3/min-ft2 ||
 * Building 1 || Block 1 || Zone 1 || 757.3 || 23913 || 658.5 || 484.8 || 173.7 || 75.2 || 56.2 || 16:00 || 87.2 || 13717.4 || 342985.6 || 1.74 ||
 * Building 1 || Block 2 || Zone 1 || 360.8 || 11515 || 313.7 || 233.5 || 80.3 || 75.2 || 55.8 || 16:00 || 88.3 || 8563.5 || 102777.2 || 1.34 ||
 * Building 1 || Block 3 || Zone 1 || 358.6 || 11415 || 311.8 || 231.4 || 80.3 || 75.2 || 55.9 || 15:00 || 88.1 || 8563.5 || 102777.2 || 1.33 ||
 * Building 1 || Block 4 || Zone 1 || 358.4 || 11408 || 311.6 || 231.3 || 80.3 || 75.2 || 55.9 || 15:00 || 88.1 || 8563.5 || 102777.2 || 1.33 ||
 * Building 1 || Block 5 || Zone 1 || 358.4 || 11411 || 311.7 || 231.4 || 80.3 || 75.2 || 55.9 || 15:00 || 88.1 || 8563.5 || 102777.2 || 1.33 ||
 * Building 1 || Block 6 || Zone 1 || 358.9 || 11428 || 312.1 || 231.7 || 80.4 || 75.2 || 55.9 || 15:00 || 88.1 || 8563.5 || 102777.2 || 1.33 ||
 * Building 1 || Block 7 || Zone 1 || 360.7 || 11502 || 313.7 || 233.2 || 80.5 || 75.2 || 55.8 || 15:00 || 88.3 || 8563.5 || 102777.2 || 1.34 ||
 * Building 1 || Block 8 || Zone 1 || 368.7 || 11819 || 320.6 || 239.6 || 81 || 75.2 || 55.6 || 15:00 || 89 || 8563.5 || 102777.2 || 1.38 ||
 * Building 1 || Block 9 || Zone 1 || 488.9 || 15588 || 425.1 || 316.1 || 109.1 || 75.2 || 55.8 || 16:00 || 88.7 || 8563.5 || 214119.2 || 1.82 ||
 * Building 1 || Roof 1 || Zone 1 || 0 || 0 || 0 || 0 || 0 || - || - || - || 159.9 || 8765.5 || 6508.5 || 0 ||